A hydrocarbon separator is intended to separate and store the free hydrocarbons contained in the runoff. These hydrocarbon separators without by-pass equipped with a sludge trap, for trapping suspended matter (sand, gravel), are ideal for treating water from covered car parks, service stations, garages. For washing areas, provide a complementary V200 stripper to obtain a volume of V300. Reminder: the oil level alarm is mandatory as additional equipment unless dispensed by the local authorities.
NF oil separator made of steel with V100 stripper, without bypass, from 1.5 to 6l/s, without closure kit - 5mg/l
The operation of the hydrocarbon separator is based on the difference-in-density separation of insoluble liquids (0.85 density) contained in the runoff water. The dewatering compartment allows the settling and trapping of suspended solids> 200μm. The coalescence system, thanks to its large surface area, allows to concentrate the free hydrocarbons by promoting their collision. The hydrocarbons then rise to the surface. The automatic shutter (float) avoids any risk of release of hydrocarbons.
- NF CERTIFIED SEPARATORS - COMPLYING WITH NF EN 858-1 AND NF P16-451-1 / CN STANDARDS - CLOTHING INTO TABLE OF WATER EXIT - POSE POSSIBLE POSSIBLE SOIL - EASY MAINTENANCE - PRODUCTS IN STOCK
- For devices without a closure kit: choose one of the 3 KN buffers listed in the table below, or refer to data sheet 4984 to select steel extensions with cast iron plugs 125 or 250Kn that are suitable.
Refer to the PHACIER manual before handling and installing the separator.
An annual inspection visit must be performed to verify the operation of the unit. It is recommended that the unit be drained when the sludge reaches 50% of the sludge's working volume or that the hydrocarbons occupy 80% of the separator's holding capacity (see NF P16-442). After each emptying, the apparatus must be re-watered and the flotation of the shutter must be checked. General maintenance instructions E104 available on our website.